1.15. 2 of the 2012 Life Safety Code says you must maintain the fire rated door assemblies in accordance with NFPA 80. Any clearance under the bottom of the door (while it is in the closed position) that exceeds ¾ inch will be considered non-compliant.
Can a fire door have a gap at the bottom?
Gaps between fire doors and the door frame should never be more than 4mm or less than 2mm. It’s recommended to aim for a 3mm gap to ensure adequate room for the intumescent strips to activate in the event of a fire, and for the smoke seal strips (if installed) to not get damaged by the opening and closing of the door.
How do you seal the bottom of a fire door?
Intumescent seals may be placed into grooves machined in the two vertical sections and top edge of the door frame. When exposed to heat, intumescent seals expand to many times their original size, sealing the gap between the door and the frame and aiding containment of the fire.
How much can you undercut a door?
In most applications, the door undercut would need to be 1.5 inches or greater to allow enough air to pass. There are some through-the-door alternatives that can be effective.
Can you lip a fire door?
It’s usually exposed top and bottom if you look at them. You won’t need to lip that.
Does a fire door have to have a threshold?
BS 9999 recommends for fire doors with cold smoke control that the threshold gap should be either less than 3mm in height or should be fitted with a threshold seal. When speaking with manufacturers, however, a common statement is that a fire doors gap of up to 8 mm underneath the door is permissible.
What should you never do to a fire door?
Top things you should not do with fire doors
- Never lock a fire door. Emergency fire doors must not be locked, or fastened in a way that they cannot easily, and immediately, be opened by any person who may require to use them in an emergency.
- Never leave a fire door wedged open. …
- Never allow a fire door to be blocked. …
- Enfield Doors.
Do FD30 fire doors need intumescent strips?
The minimum rating of a fire door is now predominantly FD30, with intumescent seals being necessary to achieve this rating. This change came about in recognition that very tight edge gaps were necessary to achieve a FD20 fire rating when doors were subjected to fire resistance testing without intumescent strips.
Why do doors have a gap at the bottom?
The gap is necessary to act as an air return when the doors are closed. Without the gap, little air will come out of the supply ductwork. It can impact the “balance” of your system.
What is door undercut?
UNDERCUT: The distance between the bottom of door and the bottom of the frame. FLOOR CLEARANCE: The distance between the bottom of the door and the top of the material directly below the door. This varies with applications, such as concrete, any floor covering and/or a threshold.
How much clearance do you need for a bathroom door?
If you central heat and air, you need the gap to be large enough for the air to get under the door when it’s closed. I usually leave about 3/4″ from the floor to the bottom of the door.
What is an undercut saw?
An undercut saw is a tool used in woodworking and construction. An undercut saw is very similar to a standard circular saw. In fact, it essentially is an upside down circular saw. Although it is used to cut materials, an undercut saw has a slightly different function and purpose than a standard circular saw.
Can I add wood to a fire door?
Hardwood is acceptable for FD60 doors BUT some hardwood species may not be used. MDF frames are NOT always allowable and MUST be checked against the door leaf’s certificate. You can fit a door closer to the door leaf/frame but it MUST be CE marked AND Certifire Approved for use on the type of door you are using.
What qualification do you need to install a fire door?
However, there is no formal requirement for people who install fire doors to have any particular qualification or accreditation, so anybody – in theory – can take on the task.
How many hinges does a fire door need?
Fire Regulations require fire doors to be fitted with 3 hinges (which must be 4 inch fire certified hinges). For doors over 2200mm tall, then four hinges can be used to prevent warping.